AMC series meters adopt AC sampling technology, which can measure the current ,voltage,power, power factor and electric energy parameters in the power grid separately. It can set the magnification through the panel membrane switch. The meters have RS485 communication interface, adopt Modbus protocol; also can convert the power signal into a standard DC analog signal.
Active energy: Class 0.5
Auxiliary power supply
Voltage: Power consumption <0.5VA;
Current: Power consumption< 0.5VA;
Auxiliary power supply:power consumption≤10VA
Single phase-2 wire,3 phase-3 wire,3 phase 4-wire
3x380V/660V(660V)(96 size only)
Note:72 profile not suitable for high voltage application
|Overload:1.2 fold rating(continuous):2 fold rating for 1 second|
|Overload:1.2 fold rating(continuous):10 fold rating for 1 second|
|Output||Electric energy||Output mode:open-collector photo-coupler pulse|
|Pulse constant:10000imp/kWh(settable),see wiring diagram for details|
|Communication||RS485 port,Modbus-RTU protocol,DLT645 protocol(versions 09 and 97),baud rate 1200-38400|
|Function||Switching input||Dry contact input,built-in power supply|
|Switching output||Output mode:Relay normally open contact output|
|Contact capacity:AC 250V/3A、DC 30V/3A|
Power:1.0 class,Reactice Electric energy:1.0 class active
Power:0.5 class,active electric energy:0.5 class,2-31th harmonic
|Power Supply||AC/DC 85-265V Power consumption≤10VA|
Between Power supply//Switching Output//Current input//voltage input and
Transmitting//Communication//Pulse Output//switching input AC 2kV 1min;
Between Power supply、switching output、Current input、voltage input AC 2kV 1min;
Between Transmitting、Communication、Pulse Output、switching input AC 1kV 1 min;
|Insulation resistance||Input、Output end to machine enclosure＞100MΩ|
Q: No display on power?
A: Check whether the supply voltage is within the operating voltage range.
Q: Incorrect reading of voltage,current,electricty,etc?
A: Checking that the voltage/current ratio setting are correct;
Checking whether the wiring mode setting is consistent with the actual situation;
Checking whether the voltage transformer and current transformer are in good condition.
Q: Abnormal communication?
A: Check whether the adress,baud rate,check bits in the communication;
Setting are consistent with the host computer;
Check whether the RS485 converter is normal;
Check the connection is corrent if the resistor above 120 ohm is connected in parallel at the communication end.
Package dimensions(1 PC)
Pakage Weight(1 PC)
WHOLE BOX PAKAGE
Package dimensions(36 PCS)
Pakage Weight(36 PCS)
PRODUCT HS CODE
The above packing and weight data are only refer to model AMC96L-E4/KC.
For other models or optional functions, please contact the salesman for details, thank you for your cooperation!
Would you like to get information about Acrel? We appreciate your interest and would be happy to advise you.Simply give us some information so we can get in touch with you
We will contact you within 24 hours.